Any installation that involves water flowing in pipes is prone for leaks. We got the first one in our robotic room. Much sooner than we would have hoped.
In the middle of a discussion with Assaf I noticed that the ceiling outside my window was "weeping" water .
A quick examination showed that the whole shelve above the window was flooded with water. We tracked this to a leaking pipe in the water-based A/C unit in the robotic room.
We called the emergency maintenance hotline, and soon someone showed up. He called the person responsible for A/C maintenance who showed up after half an hour. Together they blocked the in & out lines for this unit (and neighboring room) and drained the pipes to avoid additional leakage.
Update from this morning. The contractor who connected the A/C showed up. The fault was a fracture in valve that connected the old (pre-existing) pipes to the new installation. He replaced the valve, and now we hope that the ordeal is behind us.
For leakage, the damage was quite minimal. We might need paint renewal in few spots, but overall all equipment are intact.